PSA Homeguard HG2000 | Photoelectric Smoke Alarm 240v with 9v Battery Backup
Notify me when back in stock
HG2000 – 240V PHOTOELECTRIC SMOKE ALARM WITH 9V BATTERY BACK UP | AS3786:2014
The HOMEGUARD HG2000 is an AC powered, photoelectric smoke alarm that operates on a 240VAC power source with a 9VDC battery backup. This smoke alarm has the ability to function as a stand alone unit or in an interconnected system. This smoke alarm uses photoelectric sensing technology. Photoelectric sensing alarms may detect visible particles (associated with smoldering fires) sooner than ionisation alarms. The HOMEGUARD HG2000 includes an easy slide base plate for quick installation. The HG2000 is AS3786:2014 approved and Activfire Listed with a 5-year warranty
- Photoelectric sensing technology
- One button operation (Test & Hush feature)
- Surface mount easy slide mounting base plate
- Interconnect up to 24 units
- Tamper resistant feature
- 240VAC with 9VDC battery back-up
- AS3786:2014 approved
- Activefire listed
- 5 year limited warranty
- Must be installed by a licensed electrician
Detection Method: Photoelectric / Photo-optical sensing technology
Operation: Stand-alone or interconnect up to 24 units
Power Requirement: 240V AC 50Hz sine wave supply
Power Backup: 9Vdc battery
Rating: 80mA max per alarm
Alarm sound: 85dB at 3m
Low battery indication: Sounds a chirp at 40 second intervals, in addition to red LED flashing
Hush Function: 10-15 minutes. Red LED flash every 8-10 seconds.
Alarm duration: As long as smoke is present, unit automatically resets when smoke clears
Alarm indication: Flashing red LED indicator every second.
Temperature Range: 4˚C to 45˚C
Humidity Range: Up to 85% relative humidity (RH)
Size: 120mm Wide x 40mm High
Wiring: Active, Switch, Neutral terminal.
LED: Green, power indicator. Red, alarm indicator
Warranty: 5 years - manufacturer’s warranty
Compliance: Activfire Approved and listed to AS3786:2014 Australian standards certified product. RCM.
smoke alarm psa hg2000By: william colyer on 26 February 2018great service good price the product has worked great. had hpm smoke alarm bloody hopeless. had them for 13 months and failed